Citerm | Heating Systems
This burners are for commercial or industrial use.
The burners should be installed by an experienced installer specialized with the installation of oilfired appliances.
If you pay attention to the following hints, you will be a part of the big circle of satisfied users of: CITERM MULTI FUEL OIL BURNERS.
Waste oil may contain many foreign materials. Waste oil may also
contain gasoline. Therefore, specific precautions on the handling and
storage of waste oils are to be observed when using, cleaning and
maintaining this heater. Use a screen in a funnel when pouring oil into
storage tank to catch foreign material, i.e., gasket material and
sealant fibers, etc.
appliance is not designated for use in hazardous atmospheres containing
chlorinated or halogenated hydrocarbons. Do not expose this unit to rain
or moisture. These burners are designed to provide economic disposal of
used oils. Used oil is an inconsistent fuel and may contain water
and/or foreign materials witch may cause the unit to shut down. A
secondary source of heat should always be provided to the building.
WARNING: Do not
attempt to burn any grade of gasoline, paint thinners, or non approved
fluids. Adequate ventilation must be provided in any enclosure where
storage tanks, pump or accessories are installed.
Identical to any gas or oil burning appliance, without adequate draft
over the fire, the combustion gases cannot escape the appliance. The
flame will lengthen resulting in overheated combustion chamber. Even if
the heated is installed correctly and adequate draft. Burning used oil
is similar to burning wood. A fine gray ash accumulates in the chamber
and flue passage. This accumulation of ash will eventually affect the
draft. It is important to remove this ash before the draft is affected.
WARNING: Collect and store your oil continuously and be aware that: Water and Sludge are Not combustible! New motor oil does NOT burn!
VENTING: Failure to
provide proper venting could result in death, serious injury,
and/property damage. Units must be installed with a flue connection and a
proper vent to the outside of the building. Safe operation of any
oil-burning equipment requires a properly operating vent system, correct
provision for combustion air, and regular maintenance and inspection.
WARNING: Any cases of consequential damage due to the failure of the space heaters and boilers during operation will be excluded.
WARNING: Turn off electric power to the unit before doing any service or maintenance on the burner.